C. Clean dry sand, rock dust, or fire extinguishers, suitable from a toxic and shock standpoint, shall be provided and placed at each electrical station, such as substations, transformer stations and permanent pump stations, so as to be out of the smoke in case of a fire in the station.
D. Suitable fire extinguishers shall be provided at all (i) electrical stations, such as substations, transformer stations, and permanent pump stations; (ii) self-propelled mobile equipment; (iii) belt heads and at the inby end of belts; (iv) areas used for the storage of flammable materials; (v) fueling stations; and (vi) other areas that may constitute a fire hazard, so as to be on the fresh air side in case of a fire.
E. All firefighting equipment and fire sensor systems shall be maintained in a useable and operative condition. Chemical extinguishers shall be examined every six months and the date of the examination shall be indicated on a tag attached to the extinguishers.
F. A sufficient number of approved one-hour self-contained self-rescuers shall be readily available, not more than 100 feet away, for the persons involved in the moving or transporting of any unit of off-track mining equipment.
Code 1950, § 45-14.1; 1954, c. 191; 1966, c. 594, § 45.1-89; 1974, c. 323; 1978, c. 118; 1984, c. 590; 1985, c. 500; 1994, c. 28; 1996, c. 774; 2005, c. 3; 2015, cc. 103, 397.